EN 14511-2 PDF
BS EN Air conditioners, liquid chilling packages and heat pumps for space heating and cooling and process chillers, with. Find the most up-to-date version of EN at Engineering NBN EN Air conditioners, liquid chilling packages and heat pumps with electrically driven compressors for space heating and cooling – Part 2: Test.
|Published (Last):||24 May 2014|
|PDF File Size:||18.62 Mb|
|ePub File Size:||11.27 Mb|
|Price:||Free* [*Free Regsitration Required]|
This is a technical specification associated with ENand is used for testing the same types 14151-2 heat pumps: Testing and requirements for marking for space heating units Withdrawn.
This applies to products powered by electricity, gas or fossil fuels.
The loudness of the noise 14151-2 on the size of the room in which the heat pump is installed, its shape and its attenuation echo. This European Standard shall be given the status of a national standard, either by publication of an identical text or by endorsement, at the latest by Apriland conflicting national standards shall be withdrawn at the latest by April Although we endeavour to maintain an up-to-date catalogue, on occasion we may not have the latest version of 41511-2 document, including where it has not yet been provided through an international feed.
Standards and methods used by SP for testing of heat pumps
The length of duct and the distance of the damper from the discharge section of the unit shall 114511-2 to the requirements of EN Fite Date of publication: The data used in the calculations are based on results from a number of test points 144511-2 from capacity and efficiency testing in accordance with ENEN and EN and some additional test point.
The standard also describes testing dn reduced capacity in heating operation mode or cooling operation mode. Click here to find out how to access this document. The method applies for electrically driven heat pumps.
We recommend that you check the website of the publishers of the international document before making a purchase. The heat pump is tested and marked for the temperature condition it is intended to work at. The method is based on the calculation method in standard ENincluding domestic hot water production. Sound power 1451-2 measurements are performed at specified positions around the sound source and around a reference sound source, from which the sound power level can be calculated.
NOTE 2 For comparison purposes between reverse cycle and non reverse cycle eb, the conditions on the water side are given by the inlet and outlet water temperatures, possibly leading to different water flow rates in heating and cooling modes.
Option to visualize fn at a glance. Performance-based maintenance of air-handling systems ducts and components You may be interested in this related standard. The method is used to measure the airborne noise to the surroundings from heat pumps, air conditioners, liquid chillers and dehumidifiers when in operation.
The P-mark on a heat pump indicates that the heat pump fulfills the requirements set out in certification rules SPCR 1411-2 The method is based on the calculation method in standard EN Air conditioners; liquid chiller packs; air-to-air- water-to-air- brine-to-water- and water-to-water heat pumps can be tested in accordance with the requirements of this standard.
Test conditions, Part 3: Certification of persons Do recognize your skills, register online to become certified. Please download Chrome or Firefox or view our browser tips. Guidelines for inspection of ventilation and air-conditioning systems Modules M, M, M, M The energy savings calculated is a comparison between a house having direct 1451-2 heating and the same house having an air-to-water heat pump installed.
SS-EN Domestic hot water production.
Energy performance of buildings – Method for calculation of system energy requirements and system efficiencies – Part 3: These rules have been developed in conjunction with manufacturers and relevant authorities, and specify required performance levels such as COP, documentation 144511-2 quality assurance in manufacture. SP Method updated version. February Number of pages: The standard does not include test on electrical safety, mechanical safety, control equipment and sound power level.
SP is accredited for the method and performs tests in accordance with EN as required by ej. Measurement of fractional efficiency and air flow resistance ISO The heating coil of the heat pump is assembled in a brine bath held at constant temperature during the test. NF-mark is valid for air-to-air- air-to-water- brine-to-water- water-to-water- exhaust air- and direct expansion heat pumps.
Standards and methods used by SP for testing of heat pumps
The pressure difference between the two compartments of the calorimeter room shall not be greater than 1,25 Pa. Free to use BIM project management tool provides step-by-step help to define, manage and validate responsibility for information development and delivery at each stage of the asset life cycle in level 2 BIM projects. The marking also includes heat pumps intended for pool heating. The test involves two draw offs of half the volume of the storage tank, together with a single tapping to determine the maximum quantity of useable hot water and the reference hot water temperature.
Air-to-air, air-to-water and liquid-to-water heat pumps can be tested for approval for P-marking. The data from the test are used to calculate the system seasonal performance factor.
Get a quote for certification of systems, products or services, and get certified. The test measures performance over a period of one day, with a number of hot water draw-off periods. Their committees work with the manufacturing and service industries, government, businesses and consumers 1411-2 facilitate the production of British, European and International standards.
ISO Sound power level measuremnts. Document Status Indicators The Green document status indicator indicates that the document is: Test conditions – German version EN SP Method is a method used to calculate the seasonal performance factor of a system and 145111-2 annual energy savings of exhaust air heat pumps.
EN Test conditions_百度文库
Terms and definitions EN Follow these links to find other Standards similar to the one you are viewing. The time and energy requirements for heating up, dn use, standby power losses and overall efficiency of the equipment are measured and evaluated. Again there may be more recent versions of the document.
If you need help with the purchase or have any queries please email enquiries standards. Terms and conditions for Customized compilation of standards Een us Accessibility.